Water solenoid valve was making a weird noise when closing, manually set valve to remain open.
Performed maintenance on gas furnaces. Installed surge protector on outdoor unit, and also provided customer with an estimate to replace condensate pump.
Completed heating maintenance on 2 gas furnaces, and also humidifier.
Completed preventative maintenance on 2 gas furnaces.
Performed cooling maintenance on 2 units.
Found 35/5uf dual run capacitor failed, along with both 30A fuses. Replaced capacitor with upgraded component (5 year warranty) and installed new fuses. Tested cooling operation and removed saturated air filter.
Performed seasonal maintenance.