Drew took time to do the job correctly, efficiently, and expertly. He was very careful and made sure the work he completed was correct and that the heating system worked as intended. He took the extra time to double check on things. Great job!!!
Came out for clogged toilet. Ran an auger 8 feet and opened up the drain. Secured no more back ups.
Found the “G” wire was almost fully snipped through. The green wire was now not long enough so I used an extra brown wire at the thermostat. Switch the brown wire to g at the furnace. Turned system on and it came in properly.
Performed cooling maintenance.
Performed Biannual Cooling Maintenance
Perform Cooling Maintenances
Replaced backflow preventer