The technician was courteous, showed up on time and provided us with couple of options. Very understanding of the situation.
Thank you Tuckers for your ongoing, consistent and dependable service!
Inspected high voltage line between the outdoor unit and breaker panel. Found one wire connection missing a very small section of insulation causing the connector to short to ground. Removed existing connection with power off, replaced the connector and properly reinstalled both connections in the box. Restored power to the outdoor unit and found the unit operating properly.
Installed gas furnace, heat pump, coil, humidifier and humidifier.
Performed seasonal maintenance.
Preformed cooling maintenance on heat pump system.
Repaired outdoor unit. (Bryant unit)
2 zone Bryant Evolution system inspection
AC preventive maintenance on two Bryant systems
AC preventive maintenance on Daikin system and a air temp
AC preventive maintenance