Our technician (Ben) was very professional and knowledgeable when it came to determining the problem and ensuring it was completely repaired.
Performed cooling maintenance on 2 units.
Performed thorough evaporator coil cleaning with brushes, vacuum, chemicals, and hot water. Tested drainage and operation. Cooling is working on an 18degF deltaT, 80 degF liquid, and 54degF suction line. Indoor capacitor value is acceptable at 6.96/7.5uf.
Chemically cleaned coil.