Tuckers did a fantastic job
Replaced fuse for a minisplit.
Cleaned evaporator coil.
Performed AC maintenance on two systems.
Performed AC maintenance.
Performed ac maintenance on 2 systems.
No heat, found thermostat was tripped by breaker.
performed maintenance on heat pumps and humidifier.
Turned unit on at thermostat. Went to outdoor unit to find fan on but not compressor. Removed electrical panel to find common wire to capacitor burnt off spade. Tested capacitor, good. Replaced common wire and crimped new spade on herm wire. Restored power and cycled unit on. Experienced proper heating cycle, compressor came on
Quoted work to fix a leak
Performed seasonal maintenance.
Install aprilaire 700 humidifier
Performed Cooling Maintenances
Performed Cooling Maintenance
Air conditioning malfunctioning