Performed tankless water heater flush.
Performed seasonal maintenance.
Did a tankless water heater flush.
Performed AC maintenance on 2 systems.
Installed outdoor control board and coil temperature sensor.
Performed heating maintenance on furnace.
Installed new heat pump, air handler and humidifier.
Mrs. complained no AC. Unit on at thermostat. Went to outdoor unit to find Fan on but not compressor. Found capacitor reading low. Installed new 45/5uf capacitor. Restored power, compressor still not starting. Can hear humming noise from compressor but then cuts off. Installed hard start capacitor. Restored power, compressor came on. Amped compressor 13.9/15.2a, close to max rating. Pressures 160/460psi R-410A, extremely high. Washed outdoor coil with water and let dry. Pressures settled to 135/340psi R-410A. Temp drop 79-59=20°F. Unit is operational at this time but can hear gurgling noise compressor compressor from time to time. Compressor likely to get seized again. Recommended upgrading 16 year old AC. Mrs. agreed to upgrade estimate, office to schedule. Mrs. purchased both capacitors to have AC over weekend, no guarantees on how long system will run
Performed cooling maintenance on 2 units and installed new GAPA filters.
Preformed cooling maintenance on 2 gas furnace systems.
Preformed cooling maintenance on 2 systems.
Replaced UV bulbs