Remy was timely, professional and did a great job- would definitely use Tuckers again!
Sean and all the technicians have given us great service over the last twenty years. Sean was mentoring another tech this last time Tuckers’s came out for my spring check up. They explained everything and sold me on cleaning my coils. I’m very satisfied.
Clearly explained the issue with my system and presented all the options to fix.
Jonah did an excellent job and went above and beyond what I expected. I asked if he had a replacement cleaning brush that I accidentally broke while flushing out excess water and he fixed it for me which was greatly appreciated. He did a much more thorough job than the technician who was here in February for the winter checkup.
The employees are always friendly, knowledgeable and extremely helpful.
Trustworthy, polite and dependable.
very personable, was able to take care of us quickly and fix what we needed done literally that day. I honestly can’t say any thing bad.
Diagnosed, repaired and tested issues with toilets. Both toilets are now working properly.
Seasonal cooling maintenance and testing performed on air conditioning unit. All equipment is functioning properly at this time.
Seasonal cooling maintenance and testing performed on air conditioning unit and recommendations were made.
Performed chemical condenser coil cleaning. Equipment is clean and functioning properly at this time.
Replace draft inducer assembly
Installed new 80-gallon electric water heater with expansion tank and Honeywell tempering/mixing valve. Removed old water heater.
Performed cooling maintenance on heat pump. System operating properly at this time.
Performed combined heating/cooling maintenance on furnace/air conditioner. Systems operating properly at this time.
Performed cooling maintenance on basement and attic furnace/air conditioner. Systems operating properly at this time.
Performed cooling maintenance on furnace/air conditioner. Recommended replacement options due to age and condition of system.
Helped out customer with a cracked and inoperable thermostat. Came out, replaced thermostat, and restored operation.