Great advice as well as service. All my questions got answered and Scott got my appliance up and running,
Ken, and the team there at Crystal Blue, provided us with a great overall experience with the installation of our new AC unit. Thank you Ken for your honesty, and your follow-up... Great experience!!
Scott did a super job repairing our cooler and he has a great personality.
They did a great job.
Micheal, Justin & Keaton were awesome!! They were very professional, honest, and did an outstanding job!! Very thankful for their efforts!!
i would recommend Sean to anyone. Job well done.
I would now never call anyone else , great investigation work to get at the deep problem not just a quick fix and three months later the same problem .they worked hard to find the real culprit.
Prompt, professional and proficient!
#no Vacant building with no electricity. Needs quote on 3 systems , 1000 sqft, and two 800 sqft with kd ducting
Found out where noise is going from, water on belt. Adjusted swamp cooler pads to make water not bypass them.
Performed annual ac maintenance loomis. on Fujitsu mini split with 2 power heads. Washed interior filters. Hosed off outside unit coils of cottonwood debris. Checked drain lines of both units to the condensate pump, working well at this time. Re installed filters. Tested both units. Working well at this time Wash coils and filters more frequently to keep up efficient performance.
Installed 2 smoke alarms in the bedrooms, and uv taped the outside lineset.
Septic tank has no sanitary tee and drop leg in tank.#no will use a bit saver to drill out fitting and glue in a abs sanitary tee and drop leg. Made repairs put lid back on and backed fill
Cut in for 2100 sqft, wants industrial ductwork
#no replace 1600 sqft with ductwork
#no. 3200 sqft. Wants new cut in with ductwork
#no. Need to set for Scott and myself to come out. I had no access to roof. Need bigger ladder
Found system flat on refrigerant, outside coils very dirty my recommendation is to nitrogen pressure test system to see if thereâ€™s a big leak, than vacuum system, and factory charge system. If thereâ€™s a leak we need to address it, find it, canâ€™t just keep dumping refrigerant into system. Went to charge system and found a cracked braze at the compressor. Client wants to fix it him self then have us back out to charge system.
Performed AC diagnostic loomis. Found 32 yr old carrier heat pump not running found bad capacitor and start kit need to replace the single capacitor and start kit to try and get system running. With signing back up on our annual maintenance plan. Replaced parts and system fired up, system is running for now. 3 filters 14-24-1.
Performed annual ac maintenance Loomis. Checked refrigerant charge ok. Dual capacitor 55-5 ok, contactor ok. Disconnect ok. All electrical components ok for now. Changed 3 x 12-20-1 filters downstairs. Washed condenser coils with hose. Cycled systems on and off to verify properly functioning. System has 6 supplies and 3 returns. With 18 degree temp split at this time. Drain lines draining correctly out primary at this time. Recommendations, start amps for condenser starting to climb we can add a hard start kit or compressor saver kit to unit to help take the load off of the compressor at start up.
Could not do work.
Performed diagnostic Loomis. 21 yr old split system. Need to replace dual capacitor to get system to turn on so I can test if anything else is going on. Checked compressor windings weak. Recommend hard start kit to take the load off of the compressor at start up. And regular maintenance to try and lengthen life of system. And recommend annual maintenance.
Installed new 20-25-4 filter and left spare in attic for next time we need to replace. Took old filter to throw away