This is my go to company. They always come out same day. Our A/C went out when it was 104 degrees outside. They came out a few hours after calling them and had us up and running again in less than an hour. They have fair prices and wonderful customer service. We have used them for the past few years for repairs, yearly maintenance and they cleaned and sanitized all our vents when we first moved to our home. I can’t say enough good things about this company.
Mike and Connor were able to diagnose the problem right away and clearly explained the steps to solving it. Thanks
Same great service every time.
We were pressed for time and service and CiC made us feel important. CIC really impressed me with their experience and friendly prompt work. Thanks CIC!
Mike is always friendly and tolerant of my annoying barking dogs. Still he does a very professional job. I am very happy with the service.
Synergy the PG&E program company replaced a motor and within a couple weeks my air conditioner was blowing hot air. Did not discover until after 5:30pm and Keith’s wife was very helpful and said they would try to come the next day. They fit me in on a very hot day. Keith came and discovered motor was wired backwards. He repaired and did full check and saved the day. He was knowledgeable, friendly and efficient. No more Synergy (free is not always free) - from now on CIC only!
Excellent company, skilled technicians and excellent customer service!
Called for yearly service and problems were quickly corrected.
Diagnosed failed zone damper and added refrigerant to Lennox split system air conditioner
Replaced thermostat and added refrigerant on Lennox air conditioner.
Added refrigerant to Goodman rooftop air conditioner
Added refrigerant and replaced failing capacitors on Carrier air conditioner
Serviced 2 Lennox air conditioners and added refrigerant
Diagnosed failed capacitor on Bryant system. Replaced capacitor.
Diagnosed failed blower motor on a Rheem system. Installed new blower motor.
Diagnosed failed compressor on carrier system.
Diagnosed failed Lennox capacitor. Replaced with new capacitor.
Diagnosed inadequate installation of ductwork, losing temperature to the attic. System not cooling well as a result.
Replaced compressor capacitor on Lennox condenser.
Changed control board on Lennox furnace.
Serviced four Lennox residential air conditioners
Service and leak search on Goodman residential split system air conditioner
Seviced American Standard Air-conditioner. Changed Capacitor.