Nelson is one of your best ever. From now on we will request Nelson on any AC work.
To us it seemed like there was miscommunication from the office. David Rossi was confused that there was a problem. He was very professional, worked very hard inspite of the heat. I would recommend David.
I had water and air checked and I thought the service was very good. Both men explained what was needed to be fixed and the cost and the reason why.
Anthony and Jay did a great job. They had to remove some skirting. Jay went under the mobile home were he was directed.He had to reattach some duct that came loose and taped it in place. He also made sure all of the other duct was secure. They replaced the skirting and made sure it was in place.They were very professional and polite. I am pleased with their work. I would recommend them to anyone. I was pleased they wore their masks.Thank you so muck Bayonet Pluming-Cooling.Heating.I appreciate all you have done for me. Yours Truly, Norma Neumann
Corey was on time / early. Communications were great. Service seems to be excellent
Installed a new programmable thermostat for our A/C and ran into difficulties. Read reviews on Bayonet Plumbing, Cooling and Heating. Called and was greeted very nicely. Staff was able to schedule that same day. The text message is a nice feature. It advises you of the technician's ETA along with a name and photo. Nelson was very friendly, professional, and knowledgeable. He diagnosed the issue and had our system operational within minutes. After the system was operational, he then took the time to further check the system and made adjustments. We were so happy with the service, we purchased the maintenance package.
Tech was very knowledgeable, figured out what we needed and got it done in a short period of time. Will be going back to them for all our a/c & heating needs!
MVP tune up
Replaced T6 Pro TSTAT that was shorted on the O terminal.
Perform preventive maintenance tune up
Completed a maintenance tuneup evaluation on a single heat pump system.
Completed a routine maintenance tuneup evaluation on a single heat pump system.
Replace angle stop