Willie did a great job in explaining the issue with my air conditioner unit. His detail help me to understand my unit and how to service it in the future.
Not only was the technician timely and professional, he resolved our issue fairly quickly and explained what the problem was.
Friendly, knowledgeable, fast and even wore a mask the entire time. Fixed our air conditioner in record time.
I had Willie 3 times in the past couple years and I am always happy with his services performed
It was great. He seemed very knowledgeable. He checked everything out. Thank you
Quintin was great. He explained everything that was happening.
Found Blower motor seized, belly band for motor was broken and 25/5 cap shorted. Now system is now cooling at this time
Found capacitor dead on compressor side. Replace capacitor and system is operating/cooling at this time.
System. Or cooling found thst the condensate pump fail led to pump not allowing the system to receive voltage to operate. Replaced with new condensate pump.
System not cooling due to a bad dual capacitor on the outdoor condenser. Causing the outdoor fan motor not to run.
Upstairs system not cooling. Found the emergency drain pan filled with water tripping the float switch causing the thermostat not to have any power to operate the system.
Found system empty of refrigerant. Vacuumed system, charged it and now the system is cooling at this time.
Installed j trap and filter
System not cooling found that the start winding wire burned away from the dual capacitor. Also the thermostat was shorted not displaying temperature.
Worked on both systems. Found one needed a compressor but that system is getting expedited by another company. Found burnt wires and shorted capacitor on second system. Fixed burnt wires and changed capacitor, now the system is cooling at this time.
System not cooling main level and basement level. Found system to be low two pounds low on refrigerant.
System not cooling due to insects stopping low voltage to make the connection to power the system. Removed ants and covered contactor.
System not cooling found water in the emergency drain pan tripping the pan float switch and also found the drain line to be clogged.
System not cooling due high voltage power not powering the out door system.